Looks like I can add garbage disposals to the ever-lengthening list of household appliances that I can take apart, fix, and put back together.
Determined to debug my HVAC problems, I created a list of steps to follow. I planned to verify the presence of power and control signals at the furnace control circuit and the condenser.1Essentially, this is rule #1 of debugging electrical devices: is it plugged in?
Not feeling comfortable about my knowledge of how my HVAC is wired, I searched and found Thermostat Wire Color Codes and a thermostat wiring schematic.2Ya gotta love the Transonics wiki’s disclaimer/warning/license: “The following information may have errors; It is not permissible to be read by anyone who has ever met a lawyer. Use is confined to Engineers with more than 370 course hours of electronic engineering for theoretical studies.” I’m still trying to figure out how this applies to me.
First, I verified the 24V transformer’s primary is getting line voltage.3Yes, this means the breaker was ON and the furnace cover was off. If you’re thinking of using my post as a guide to debugging your HVAC system, you should read the preceding footnote. Then, checking the secondary, I found no voltage. I tried again. I pulled it out of the furnace and tried again. Still no dice. I guess I could have just measured the impedance across the secondary and discovered the transformer was bad4 and needed replaced.
Unfortunately, by the time I discovered this, the local appliance parts and electrical supply stores were closed for the week. Home Depot and Lowe’s were still open but neither has a matching transformer. Looks like it will be next week before our HVAC is working.4It was shorted.
I’m concerned: if I replace the transformer, is something else wrong that will kill the new one? Or did the transformer just die of old age? I guess I’ll find out.
Fortunately, the weather is getting cooler.
Our HVAC stopped working in the hottest week of the summer (so far…). Rather than call an HVAC tech, I’m trying to fix it myself.1After all, what could go wrong? ;-)
Symptoms: no fans start running even though the thermostat is correctly set (and for that matter, fan set to “on”).
Checks so far:
- Thermostat batteries
- Short yellow to red and wait two minutes
- Interrupter by condensor
- Look for fuses in furnace control circuit and interrupter (there were none)
At this point, I think it’s time to verify voltages and signals, starting with the transformer and furnace control circuit, then moving outside to the condensor.
Wish me luck!