Doing some work on our furnace, I had the opportunity to take a picture of the blower.1 And, thanks to this work, I now have a much better understanding of the sensors, switches, blowers, and valves, and how they all interact. So cool!
I’m looking forward to spring when I get to do the same sort of maintenance on the air conditioner.
In the fall an old man’s fancy lightly turns to thoughts of debugging HVAC systems.1 Unfortunately, not only in the fall. Now it’s the heating portion. A few Augusts ago, it was the cooling portion. The resources I found then will come in handy.
Determined to debug my HVAC problems, I created a list of steps to follow. I planned to verify the presence of power and control signals at the furnace control circuit and the condenser.1
Not feeling comfortable about my knowledge of how my HVAC is wired, I searched and found Thermostat Wire Color Codes and a thermostat wiring schematic.2
First, I verified the 24V transformer’s primary is getting line voltage.3 Then, checking the secondary, I found no voltage. I tried again. I pulled it out of the furnace and tried again. Still no dice. I guess I could have just measured the impedance across the secondary and discovered the transformer was bad and needed replaced.
Unfortunately, by the time I discovered this, the local appliance parts and electrical supply stores were closed for the week. Home Depot and Lowe’s were still open but neither has a matching transformer. Looks like it will be next week before our HVAC is working.4
I’m concerned: if I replace the transformer, is something else wrong that will kill the new one? Or did the transformer just die of old age? I guess I’ll find out.
Fortunately, the weather is getting cooler.
Our HVAC stopped working in the hottest week of the summer (so far…). Rather than call an HVAC tech, I’m trying to fix it myself.1
Symptoms: no fans start running even though the thermostat is correctly set (and for that matter, fan set to “on”).
Checks so far:
- Thermostat batteries
- Short yellow to red and wait two minutes
- Interrupter by condensor
- Look for fuses in furnace control circuit and interrupter (there were none)
At this point, I think it’s time to verify voltages and signals, starting with the transformer and furnace control circuit, then moving outside to the condensor.
Wish me luck!